TapSnap Flushing Surveillance Monitor
The world’s first water outlet flushing surveillance monitor!
"Flushing makes a big impact on the levels of bacteria, including Legionella, in showers, taps, etc. Anything that would help people spot low-use water outlets, and tell them when to flush would be useful."
- Simon Dooner
Director, Legionella Control International
TapSnap is a low-cost tool to verify a water outlet has been flushed within a specific time. It provides a visual reminder to flush outlets, removing bacteria that may be growing in stagnant water. Within healthcare facilities, TapSnap monitors help reduce the risk of waterborne infection and supports CMS-mandated Legionella water management programs.
Innovative Design Detects and Monitors Water Flow
The TapSnap monitor is a patent-pending design utilizing a unique vibration sensor combined with a timer and LED light. It’s all packaged into a small enclosure that attaches directly to showers, eyewash stations, and faucets for easy installation, removal or repositioning. The embedded sensor detects vibration caused by water flow through the outlet and starts a timer. The battery-powered monitor acts as both a stagnation and flushing timer alerting users when to flush an outlet and for how long. Stagnation times can be set to 1-week or 1-month.
How It Works
Easily snaps on standard round diameter water outlets (0.68" - 0.88")
Green "heartbeat" LED confirms
monitor is working
Highly visible green/red LED indicators
Works on low-flow or high-flow outlets
Small, compact design
Low-battery indicator. Easy to replace
"Smart" flushing timer - longer stagnation requires longer flushing
Selectable stagnation timer - 1 week or 1 month
Does not contact the water flow
Battery-operated, no power cords
Splash-proof and water resistant
Quick to install, remove, or relocate
"Since the monitors have been installed it has reminded staff to flush the lines when the sensor flashes red.......I would like to eventually see these sensors on all eye wash stations and showers."
- Aloyoise MacNaught
Stephen's Memorial Hospital
Use on high-risk faucets with spray aerators (e.g. OR scrub sinks) or attached eyewash stations.
Perfect for rarely used staff or patient showers - either hand-held showers with hose loops or wall-mount showers.
Eye Wash Stations
Fits on multiple styles - from stationary to swing-in-place or faucet-mounted versions.
When should I consider using a TapSnap monitor?Monitors are best deployed on water outlets known or suspected to be unused for more than 5 days. If usage is unknown, the monitors can be used to roughly determine outlet usage in weekly increments from 1 - 4 weeks.
How do I purchase larger quantities of TapSnap monitors?Contact customer support at email@example.com or call 970-646-3351 to ask questions or place an order. There are discounts for higher volume orders.
What type of warranty do you offer?TapSnap monitors come with a 90-day warranty.
What type of battery does it use and how do I replace them?TapSnap monitors use a 1/2 cell AA battery. They are commercially available or you can order replacement batteries by contacting us at firstname.lastname@example.org or call 970-646-3351. We have the best prices on batteries proven to work best with the monitors.
Are there any water outlet flow rate requirements?TapSnap sensitivity is optimized for low-flow outlets, but if the water flow rate is too low, the monitor may have difficulty sensing vibration. We recommend flushing outlets using the highest flow rate (i.e. full flow). In some cases the monitor may need to be repositioned to improve sensitivity.
I have a non-standard water outlet dimension. How do I get a TapSnap monitor that fits my water outlet?If the diameter of your water outlet is too small or too large for the standard TapSnap monitor we can provide a spacer or a larger battery cover/clip. We can also 3D print a limited quantity of attachments with different configurations. Contact us at email@example.com for more information. Circular outlets should be 0.68" - 0.8" to fit the standard TapSnap monitor.
Where is the best place to install the monitor on an outlet?The best place to install a TapSnap monitor is towards the free or distal end of the water outlet or after a turn or bend in the outlet. The monitor can also be attached directly to shower hoses. In most cases, water flow through the outlet will be enough to trigger the monitor, regardless of the location. You may need to experiment to find the best sensor position.
How do I know when the water outlet has been flushed long enough?The red LED will turn off, replaced by a flashing green LED when the water outlet has been flushed long enough. Flushing times are variable when the monitor is set to a 1-week stagnation time and will vary from 30 - 120 seconds depending on how long the outlet has been stagnant. When the monitor is set to a 1 month stagnation time, flushing for 2 minutes is required to reset the monitor to green.
What happens if the TapSnap monitor gets wet?TapSnap monitors are splash-proof and water resistant. They will definitely get wet, but don't worry! They are designed for wet environments. They work great on faucets, eye-wash stations and even in warm, humid showers.
Who do I contact if I still have questions about TapSnap monitors?Contact Customer Support at firstname.lastname@example.org or call 970-646-3351 to ask questions or place orders.